Electric power utilities with aging infrastructure face increasing risk of blackouts and brownouts. By using FLIR thermal imaging cameras and automation software, impending equipment failures and security breaches can be detected anytime, day or night, at a remote monitoring location.
Failure cause and effect
The risk of blackouts and brownouts are increasing on the power distribution grid due to aging infrastructure, and a lack of automation systems that monitor the condition of critical equipment at substations and elsewhere on the grid.
For example, transformer fluid leaks or internal insulation breakdown cause overheating that leads to failures, but many utilities don’t have automated thermal detection systems that reveal these problems.
Whatever the cause, a critical substation failure may cascade into series of failures. The result can be a massive failure of banking facilities, security systems, manufacturing plants, food refrigeration, communication networks, and traffic control systems. Of course, an electric utility involved can lose huge amounts of revenue and incur enormous costs in getting their systems up and running again.
Thermal imaging cameras help to save money
Thermal imaging technology can improve the reliability and security of electric substations. Although electric utilities have for many years used handheld thermal imaging cameras to monitor substation equipment, quite some are now turning to permanently installed thermal imaging camera systems. Through the use of automated thermal imaging cameras and innovative software, FLIR and its partners have developed monitoring systems that provide early warning of impending equipment failures.
These systems employ advanced sensing and measurement technology, control methods, and digital communications. They are able to anticipate, detect, and respond rapidly to problems, thereby reducing maintenance costs, the chance of failure, a blackout, and lost productivity.
Just one example: one large utility discovered a hot bushing rod in a substation transformer and repaired it at a cost of only €12,000. A similar problem that occurred before the firm instituted its thermal imaging program resulted in a catastrophic failure that cost more than €2,250,000.
A few substation components whose thermal signatures are precursors to failure
– Power transformers (oil levels and pump operation)
– Load tap changers (oil levels, other internal problems)
– Insulator bushings (oil levels and bad connections)
– Standoff insulators (moisture, contamination, degradation)
– Lightning arrestors (degradation of metal oxide disks)
– Circuit breakers (oil or SF6 leakage)
– Mechanical disconnects (bad connections, contamination)
– Control cabinets (wear and tear on fans, pumps, and other components)
Detection of temperature increases in these components with thermal imaging cameras allows preventive maintenance operations before an unplanned outage occurs due to outright failure.
Principles of thermal imaging
The first principle of thermal imaging is “many components heat up before they fail”.
Second, all objects emit thermal radiation in the infrared spectrum that is not seen by the human eye.
Third, thermal imaging cameras convert that radiation to crisp images from which temperatures can be read. This non-contact temperature data can be displayed on a monitor in real time, and can also be sent to a digital storage device for analysis.
Thermal imaging cameras do not require light to produce images, and can see hot spots well before excessive heat or loss of insulation leads to failure. They can be mounted in all-weather housings and placed on pan/tilt drive mechanisms to survey large areas of a substation. Due to FLIR’s wide selection of lenses with different focal lengths. Therefore, they support 24/7 monitoring in all types of weather and locations.
FLIR thermal imaging cameras recognise differences in the heat signatures of electrical components and the surrounding background (such as the sky or clouds), and can compare the temperatures of similar components in close proximity to one another. Built-in logic, memory, and data communications allow them to compare the temperatures in their images with user-defined settings, and send that data to a central monitoring station for trend analysis, triggering alarms, and generating exception reports. They can even notify facility managers in remote offices of abnormal conditions by triggering an email message. This makes them ideal for unattended monitoring of substation equipment.
Typical system configurations
In co-operation with automation system suppliers FLIR Systems works to create customized thermal imaging and noncontact temperature measurement systems for electric substations.
These systems can automatically perform site patrols, monitor equipment temperatures without human supervision. The video images and their temperature data are carried over Ethernet, wireless, or over fiberoptic cables to an appropriate interface that communicates this data to the central monitoring location.
The schematic diagram depicts a typical substation monitoring system that uses FLIR A310 thermal imaging cameras. Systems of this type have been installed at substations worldwide. The most advanced versions of these systems provide time-stamped 3-D thermal modelling of critical equipment and areas.
FLIR A310 is a fixed mounted thermal imaging camera. It can be easily integrated in an all-weather housing and installed almost anywhere to monitor critical equipment and other valuable assets. It can safeguard your substation and measure temperature differences to assess the criticality of the situation. This allows you to see problems before they become costly failures, preventing downtime and enhancing worker safety.
– Built-in extensive analysis functions
– Built-in alarm functions
– Ethernet/IP and Modbus TCP compliance
– Easy sharing of analysis, alarm results to PLC’s.
– PoE (Power over Ethernet)
– Digital inputs/outputs
– Built-in 100 Mb Ethernet connection.
FLIR Systems India Pvt Ltd
1111, D Mall, Netaji Subhash Place,
Pitampura, New Delhi – 110034
Tele: +91-11-4560 3555
Fax: +91-11-4721 2006